Can I retrofit MVHR?
Fitting MVHR systems into existing properties is challenging, for a couple of reasons: –
The fabric of the building needs to be virtually airtight – hence windows often must be replaced/upgraded, trickle vents removed.
You will need to route 75 or 90mm ducting to every room of the property back to the location of the main unit.
Having said that if you’re determined it can be done. It is easier to retrofit MVHR into a bungalow. We can advise you as to whether it is possible to retrofit your property.
More Questions About MVHR
Is a MVHR system noisy?
A properly designed MVHR system should be very quiet in its operation with air flows calculated to move the correct volume of air for each room without causing a whistling or noises pertaining to the movement of the air.
What does the heat recovery part of MVHR mean?
The systems that we offer retain between 90 and 95% of the heat in your home while exhausting the stale air from your property to outside.
There is a heat exchanger within the unit that passes the heat to the new fresh air entering the property while exhausting the stale air back to the outside.
Where is the MVHR unit and system installed?
The MVHR unit can be installed in a large cupboard or possibly the loft space. From the unit there will be 75mm and 90mm ductwork travelling to all the rooms in the property.
There are also 2 larger 160-180mm pipes that need to go outside through a wall or roof vent, providing incoming and outgoing air.
What makes of MVHR do you supply and install?
We offer both Zehnder and Vent Axia products. Both manufacturers are leading MVHR suppliers that each have their own qualities and warranties.
How much does MVHR cost to run?
It costs approximately £30 – £55 per year in electricity to run a large MVHR system constantly, but you save a lot more than that on heating bills because it is recovering the heat that would normally be exhausted by traditional extractor fans and draughts from trickle vent windows etc.